When discussing temperature efficiencies, it is important to differentiate between dry and wet temperature efficiencies.
A dry temperature efficiency of 85 per cent is equivalent to a wet temperature efficiency of over 90 per cent. The wet temperature efficiency is theoretical and may not work in practice due to freezing. We have tried to illustrate this in the diagram below.
Energy recovery, counter-flow exchanger
Do not be misled by various "marketing tricks" that specify different efficiencies for the same heat exchanger.
We always specify the dry efficiency, which is also the only efficiency that can be measured during an inspection.
Same heat exchanger reported on in different ways
|Dry, in accordance with EN308 (correct!)||85 %|
|Wet incl. motor heat||88–95 %|
|Annual energy incl. motor heat||92–97 %|
Others also read
Smart ventilation creates new possibilities
Innovative ventilation solutions can add value to your project. Here are three possibilities that you may not ha...
Smart ventilation increases property value
The thinking concerning the benefits that arise with good ventilation has changed over the years. Ventilation ha...
Indoor climates are affecting performance
Hot summers and cold winters are something many wish for – except when...
How to cool a building in the best way
In this comparison between four different options, we look at energy efficiency, installation complexity, noise ...